Designed to alert building owners to flat roof leakage and ingress, the International Leak Detection (ILD) waterproofing integrity testing system has provided reassurance for two decades. Sika finds out more…
Flat roof design has many advantages: it can result in lower building costs, and allows for potential development. The space can be transformed into a Solar or Green Roof, for example.
However, flat roofs are more prone to water ingress than pitched roofs, which can quickly shed waste water by design. Many designers, building owners, facilities managers and tenants fear leakage, which can be costly to combat.
In 1996, the International Leak Detection (ILD) was founded to solve this issue. As a waterproofing integrity testing system, ILD involves a trio of techniques.
The first, Electric Field Vector Mapping (EFVM) testing, is carried out by applying water on the surface of a roofing membrane to create an electric field. The water is then used a conductive medium; any breaches in the membrane will cause an electrical connection to occur.
ILD inspectors are able to follow the directional current of the flow to establish its point of entry.
The second technique, ProtectSys ‘B’, comprises an electro-conductive material, contact plates and contact boxes. The system is placed beneath the waterproofing membrane; should any moisture enter into its level, it will be able to determine the location of the defect.
ILD’s ProtectSys ‘WM’ early warning system utilises radio signals to measure temperature and relative humidity inside and outside a roof’s insulation layer. The measurements are transmitted to a central unit via radio signals; they are then mailed to a central computer by G.S.M, where the condition of the roof is analysed.
ILD has been guaranteed as a fault detection system: although there can be no absolute assurances against water ingress with flat roofs, ILD can prevent minor problems from developing further.
The non-woven glass fleece should then be loose laid to the upper surface of the insulation boards, before the two contact plates can be fitted into the individual roof area (additional contact plates are required when the roof space exceed 1,500 square metres).
Contractors should then install two cable access duct components as close to the contact plates as possible. The contact plate cable must be brought up through the proprietary cable access duct component to allow the testing ILD technician access.
The single ply roofing membrane can then be fitted to the surface of the insulation boards.
Welwyn Garden City,
Phone: 01707 394444
Fax: 01707 329129
Bull Products has strengthened its presence in the shipbuilding industry, after securing a partnership with a major Norwegian distributor.Posted in Articles, Building Industry News, Building Systems, Case Studies, Facility Management & Building Services, Health & Safety, Posts, Security and Fire Protection, Site Preparation
Following the coming together of Icopal and Monier Redland, and a period of investment in premises, systems and people, BMI UK & Ireland has been formally launched to the construction industry.Posted in Articles, Building Associations & Institutes, Building Industry Events, Building Industry News, Building Products & Structures, Building Services, Building Systems, news, Posts, Restoration & Refurbishment, Retrofit & Renovation, Roof Edge Protection, Roofs
The MCRMA has published an Advice Note titled AN 4: The Building (Amendment) Regulations England 2018.Posted in Articles, Building Associations & Institutes, Building Industry News, Building Products & Structures, Building Regulations & Accreditations, Cladding, Health & Safety, Posts, Publications, Roofs, Security and Fire Protection, Walls
With heavier materials and darker colours being used in more and more projects, Troldtekt is exploring the movement in detail in its latest Theme.Posted in Acoustics, Noise & Vibration Control, Articles, Building Industry News, Building Products & Structures, Ceilings, Innovations & New Products, Interiors, Paints, Coatings & Finishes, Posts