Ethan Thompson, product manager at Heatrae Sadia explains what you need to know about selecting products for a heat network in the latest issue of ABC&D Magazine.
Communal heating is becoming increasingly popular for developments with multiple dwellings, but what do architects need to know when it comes to specifying these schemes, and what should they look out for when selecting products for a heat network?
Communal heating schemes (sometimes referred to as community heating, district heating or heat networks) provide heat to individual properties from a centralised plant through a distribution network.
In recent years, the concept has become more widely adopted, particularly in multi-occupancy high rise schemes such as apartment blocks. In these developments, centralised schemes can offer benefits over the more traditional solution of installing separate heating systems in each individual property.
In particular, efficiencies can be increased and fuel consumption can be reduced. In fact, compared to alternative solutions, centralised plant systems are particularly well- positioned to help developers meet their required targets in a cost-effective way.
Using a centralised plant also decreases the risks linked to gas distribution pipework and eliminates the need to fit numerous flue terminals and plume displacement and condensate drainage systems, potentially reducing capital installation costs, depending on the size of the development.
Heat interface units (HIUs), also known as heat boxes, will generally be used to provide the heating, or heating with domestic hot water, to individual properties, with the householder controlling their use of heat with either a room thermostat, a separate programmer or individual thermostatic radiator valves.
When using a central boiler plant and HIUs, cascade systems can be considered within the design, supporting more efficient systems and lower return temperatures. In all cases, the boiler plant must be capable of delivering peak space heating load. However, HIUs incorporating a plate heat exchanger for domestic hot water require special consideration, as generally there will be a significant difference between heating and hot water loads.
For example, heat loads for each dwelling could be in the region of 3-5kW, whereas 35kW or more is likely to be required for peak domestic hot water. For an economical and energy efficient solution to be achieved, appropriate coincidence factors need to be adopted so as to realise the benefit from the diversified load when determining plant capacity – in most cases this will involve consideration of the occupants’ lifestyles and typical use profiles.
There is certainly no one-size-fits-all solution. Indeed, the success of a communal heating scheme largely depends on it being sized and designed appropriately for the demand of the building, and whether both the peak and base loads have been properly considered.
If oversized, it won’t just be the central plant that is too large; inevitably, other elements such as the pipework, distribution pumps, expansion vessels and inhibitor volumes required to protect the system (to name just a few) will increase.
When selecting HIUs for a scheme, architects should look for independent third-party approvals to ensure that products comply with industry standards and regulations. For example, the NEMKO mark demonstrates that a product has been assessed for conformity to electrical safety legislation by a competent body, providing reassurance to the specifier and assisting compliance under CDM regulations. Meanwhile, independent testing for water fittings guarantees that products are safe to use and will guard against the contamination of potable water supplies. Here, the industry standard third-party certification is provided by WRAS or KIWA.
Some HIUs feature a compact design (to fit into a standard kitchen cupboard) and comprise two generously-sized plate heat exchangers – one for the hot water and one for the heating system. They are designed to ensure that the primary return temperatures going back to the centralised heating system are very low to maximise the operating efficiency of the system. PID controllers modulate flow to the units in order to optimise performance, working with the room thermostat. They are suitable for single and dual zone heating systems.
In recent times, there has been a trend towards centralised plant being used to deliver heating and hot water to individual properties in developments such as apartments and community housing. This approach offers many benefits, including increased efficiency and lower installation and maintenance costs, making them a suitable choice for architects working on multi-dwelling projects.
Alcumus has released two new Association for Project Safety (APS) accredited courses, designed to offer businesses a better legal understanding and practical guidance on The Construction Design and Management (CDM) Regulations 2015.Posted in Articles, Building Industry Events, Building Industry News, Facility Management & Building Services, Health & Safety, Posts, Publications, Site Preperation
Wienerberger has increased its product offering with the launch of a new Kassei KTF clay paver.Posted in Articles, Bricks & Blocks, Building Industry News, Building Products & Structures, Civil Engineering, Garden, Hard Landscaping & Walkways, Landscaping
Recofloor is now accepting entries for its 2018 Awards Event which is set to take place in April at Liverpool Football Club’s Anfield ground.Posted in Awards, Building Industry Events, Building Industry News, Building Regulations & Accreditations, Posts, Site Preperation, Waste Management & Recycling