Euroroof BUR Warm Roof System has been specified for use in the refurbishment of a damaged pitch roof construction on Edgewood Road.
78c-100a Edgewood Road is a multi-functional development, which comprises single floor retail establishments and two storey residential properties.
Its original pitched roof construction, which was finished with a bitumen felt waterproofing system, was in need of attention. Upon carrying out a full site inspection, Alumasc discovered that several failed repair attempts had been undertaken.
The company identified several serious instances of failure, including numerous points of splitting and tearing of the original membrane. The system’s deterioration had also exposed the decking, exposing it to the elements and compromising its structural integrity.
Deflections between the rafter centres indicated that the decking was damaged; the material suffered high levels of water entrapment in multiple locations.
Following its assessment, Alumasc deemed the saturated decking board a danger to the establishment’s occupants and operatives. As it was no longer classified as a suitable structural solution, the board needed to be removed and replaced with an alternative.
To fix the development’s roofing system, the deck was removed and replaced with a Plywood/OSB3 deck, which complies with current Building Regulations and Alumasc’s recommendations.
New timbers were cut in to replace areas of the frame that had suffered from dry/wet rot, restoring the building’s structural integrity before the installation of the new decking material.
The Euroroof BUR Warm Roof System was specified to replace the original, failed system, allowing the building to achieve its required minimum U-value of 0.18 W/m²K.
To fit the curved profile of the development’s pitched roof, the system was supplied in bespoke manufactured rolls, which were installed to pre-determined roll lengths to increase coverage and minimise site waste.
Applied in ZK primer, Euroroof Self Adhesive Vapour Control Layer (SAVCL) PLUS was used in the strip and replacement of the decking to limit potential fire risk throughout the course of the refurbishment. Once the combustible materials had been encapsulated, torch applied membranes were used.
Off Station Road,
Phone: 01536 383865
Fax: 01536 72685
Kalzip has had its FC rainscreen facade system tested in accordance with BS 8414-1 and has successfully met the requirements of BR 135.Posted in Articles, Building Industry News, Building Products & Structures, Building Regulations & Accreditations, Building Systems, Facades, Research & Materials Testing, Retrofit & Renovation, Security and Fire Protection, Walls
To recognise International Women’s Day on 8 March, safety expert OnSite Support has announced the measures it is taking to support women in construction.Posted in Articles, Building Industry Events, Building Industry News, Health & Safety, news, Plant, Equipment and Hire, Training
Keyline Civils Specialist has joined the Government’s Kickstart Scheme – a placement programme designed to support young people into the workforce.Posted in Articles, Building Industry Events, Building Industry News, Building Products & Structures, Building Systems, Civil Engineering, Facility Management & Building Services, news, Posts, Recruitment, Training
Hush ActiV, C-TEC’s innovative new BS 5839-6 domestic fire alarm system, is providing first-class fire protection at a luxury apartment block in Bolton.Posted in Articles, Building Industry News, Case Studies, Facility Management & Building Services, Health & Safety, Innovations & New Products, Security and Fire Protection