Concerned by water tightness failures in alternate roofing underlays, DuPont Tyvek instigated an independent field test to examine the ‘real world’ performance of its systems.
After hearing reports of alternate vapour-open roofing underlays leaking, DuPont Tyvek issued an investigation into the ‘real world’ performance of these systems.
Martin Peifer, an independent expert of Steildach-Technik GmbH, was contracted to collect underlay samples from 30 different roofs.
These roofing underlays were exposed to rigorous water tightness tests at the Kiwa GmbH TBU laboratory; the tests were designed to examine how each underlay has aged in the ‘real world’.
Whilst the ageing process can have a positive impact on vapour diffusion, it can adversely affect an underlay’s water shedding function should the primary covering fail. In stormier weather, this is a common occurrence.
Each sample was subjected to a 20cm water column for two hours. Experts assessed whether any leakage had occurred; if so, how much, over what surface area and how quickly. The EN13859-1&2 classification system for water tightness was used to determine how well each roofing underlay endured water after 5 to 10 years in situ.
Following the tests, 13 out of the 17 Tyvek underlays examined were declared watertight, after more than 20 years in a roof. The Tyvek samples were significantly older than the other installed products, demonstrating their durability.
Meanwhile, 2 out of the 7 coated roofing underlays tested could be declared watertight after less than 10 years; none of the multi-layer microporous based roofing underlays achieved water tightness.
DuPont Tyvek argues that a roofing underlay’s primary quality, in terms of longevity, is water tightness – underlays which fail to provide this are putting property and insurance at risk.
The company believes that current building and industry codes, with their focus on mechanical stress, are misleading. Homeowners are more likely to benefit from long-term water hold out; assessment methods still lag behind in evaluating this.
DuPont Protection Solutions
Bristol & Bath Science Park
Phone: 08444 068 722
Technical enquiries: [email protected]
As part of its own contribution to improving air quality, NHS Property Services chose to replace the roof of the Hattersley Health Centre in Hyde, Greater Manchester, with the help of BMI.Posted in Articles, Building Industry News, Building Products & Structures, Case Studies, Health & Safety, Posts, Restoration & Refurbishment, Retrofit & Renovation, Roofs, Sustainability & Energy Efficiency
Project Specification Group, a unit of ASSA ABLOY Opening Solutions UK & Ireland, says the drive to reduce cost must not be allowed to compromise the safety performance of a building, ahead of Fire Door Safety Week.Posted in Access Control & Door Entry Systems, Articles, Building Industry Events, Building Industry News, Building Products & Structures, Building Regulations & Accreditations, Doors, Exhibitions and Conferences, Health & Safety, Security and Fire Protection, Seminars
Aggreko has developed its new Dryer DewPoint Monitoring System for its Oil Free Air Compressor product line.Posted in Articles, Building Industry News, Building Services, Heating Systems, Controls and Management, Heating, Ventilation and Air Conditioning - HVAC, Innovations & New Products, Posts
How do you ensure a fresh, comfortable environment in an internal space the size of 11 football pitches, which can accommodate the transfer of up to 55 million people a year? Gilberts Blackpool have the answer…Posted in Air Conditioning, Articles, Building Industry News, Building Services, Case Studies, Heating, Ventilation and Air Conditioning - HVAC, Restoration & Refurbishment, Retrofit & Renovation